|2017-03-09||Other||Schneider Electric||Sergey Temnikov and Vladimir Dashchenko of Kapersky Labs Critical Infrastructure Defense Team identified and reported the vulne||N/A||CVE-2017-6021 ||N/A||N/A||N/A|
# Schneider Electric ClearSCADA
### VULNERABLE VENDOR
### VULNERABLE PRODUCT
Sergey Temnikov and Vladimir Dashchenko of Kapersky Lab's Critical Infrastructure Defense Team identified and reported the vulnerability to Schneider Electric.
### AFFECTED PRODUCTS
The following versions of ClearSCADA, server and communications driver processes, are affected:
All supported versions including:
ClearSCADA 2014 R1 (build 75.5210) and prior,
ClearSCADA 2014 R1.1 (build 75.5387) and prior,
ClearSCADA 2015 R1 (build 76.5648) and prior,
ClearSCADA 2015 R2 (build 77.5882) and prior.
Successful exploitation of this vulnerability could cause the ClearSCADA server process and communications driver processes to terminate.
### VULNERABILITY OVERVIEW
IMPROPER INPUT VALIDATION CWE-20
An attacker with network access to the ClearSCADA server can send specially crafted sequences of commands and data packets to the ClearSCADA server that can cause the ClearSCADA server process and ClearSCADA communications driver processes to terminate.
CVE-2017-6021 has been assigned to this vulnerability.
A CVSS v3 base score of 7.5 has been assigned; the CVSS vector string is (AV:N/AC:L/PR:N/UI:N/S:U/C:N/I:N/A:H)
Critical Infrastructure Sector(s): Critical Manufacturing
Countries/Areas Deployed: Worldwide
Company Headquarters Location: Paris, France
Schneider Electric has released the following updates to mitigate the vulnerability:
ClearSCADA 2014 R1.1 hotfix build 75.6239
ClearSCADA 2015 R1.1 Service Pack (build 76.6191)
ClearSCADA 2015 R2 hotfix build 77.6181
Users of ClearSCADA 2013 R2 and prior versions should upgrade to the latest ClearSCADA 2015 R2 hotfix to mitigate the vulnerability.
Each of the Service Pack and hotfixes above are available for direct download from Schneider Electric's web site at:
More information can be found by visiting Schneider Electric's Security Notification at:
Schneider Electric recommends users include the following measures in their SCADA strategies:
Secure physical and network interfaces to the ClearSCADA system.
Deploy suitably configured firewalls between network segments to limit access to ports and protocols appropriately.
Deploy VPN technology with secure authentication on any externally accessible networks.
Configure and audit user security to reduce the risk of a denial of service.
For critical accounts use ClearSCADA security policy configuration to disable invalid logon count and delayed lockout time and to use logon throttling.